Fujitsu Inverter AC Error Codes
Fujitsu AC error codes
fujitsu air conditioner error codes
Fujitsu ducted air conditioning
Fujitsu Wall Mounted Air Conditioner
Fujitsu Ceiling Cassette Air Conditioner
Fujitsu AC error codes,This model is a non-insulated PCB that does not take the insulated structure on the PCB from this financial year. Be aware that it is likely to hug when it touches the charged part at the time of examination. In addition, there is a possibility of shock even when the display PCB or stepping motor, etc., touch the secondary circuit.
Fujitsu AC Remote Controller Wired Error Code
When EE: EE is displayed on the remote control, press the “Energy Save” and “Zone Control” buttons simultaneously for more than 3 seconds. The fault code will then be displayed on the LCD.
Error code meaning
E0: 00 com error – remote from indoor
E1: 00 com error – indoor to outdoor
E2: 00 Return Air Thermistor Open Circuit
E 3: 00 return air thermistor short circuit
E4: 00 indoor coil thermistor open
E5: 00 Indoor coil thermistor short
E6: 00 outdoor coil thermistor open
E7: 00 outdoor coil thermistor short
EA: 00 Outdoor Ambient Thermometer Open
Eb: 00 Outdoor Ambient Thermistor Small
Ec: 00 discharge pipe themster open
Ed: 00 discharge pipe thermistor shorted
EE: 00 high pressure problem
EF: 00 discharge pipe temp. Problem – too much = lack of gas
OO ID to RC Comms Fail
OD Comms from O1 ID failed
O2 ID Air Sensor Open
O3 ID Air Sensor Lock
O4 id pipe sensor open
O5 ID Pipe Sensor Lock
O6 OD pipe sensor failed
O8 power source connection failure
O9 drain problem float switch operated
OA OD Air Sensor Failed
OC discharge sensor fails
OE Outdoor High Pressure Heat Sink Error
11 OD PCB failed
12 ID Fan Fail
13 OD signal abnormal ID signal error
14 OD Fail
15 compressor temporary failure
16 pressure switch error
17 ipm error
18 ct error
19 active filter module error
1A Compressor Failure
1B OD Fan Failure
1C inverter failed for PCB controller
1d2 way valve sensor sensor failed
1E Expansion Valve Error
1F Connection ID Unit Error
20 indoor manual switch unusual
24 Extremely high pressure protection upon cooling
25 pfc circuit error
26 indoor signal error
27 indoor signal error
28 indoor heat exchanger temperature error
29 outdoor heat exchanger temperature (middle) error
2A power supply frequency detection error
2B Compressor Temperature Error
2C four-way valve abnormal
Press the “Energy Save” and “Zone Control” buttons simultaneously for more than 3 seconds to return to normal operating mode.
Fujitsu Air Conditioner Operation Light Flashing
Red light operation green light timer current model
Off Red light 2 Flashes green light Reverse Comms Fail at Startup
Off Red light 3 Flashes green light Comms Fail In Use
Off Red light 4 Flashes green light Comms Fail at Startup
Off Red light 5 Flashes Forward Comms Fail In Use
Off Red light 8 Flashes green light Wired Remote Control Failure
2 flashes 2 flashes green light indoor air sensor failed
2 flashes 3 flashes green light indoor pipe sensor failed
2 brightness 4 brightness green light indoor heat exchanger sensor error
2 glow 6 glow green light float switch operated
3 flashes Red light 2 flashes green light OD switch sensor failed
3 flashes Red light 3 flashes green light OD pipe sensor failed
3 flashes Red light 4 flashes green light OD air sensor failed
3 flashes Red light 7 flashes green light heat sensor error
3 flashes Red light 8 flashes green light compressor floating sensor failed
4 flashes Red light 2 flashes green light forced welded auto switch
4 Shine Red light 3 Shine green light Welded Main Relay
4 flashes Red light 4 flashes green light power failure
4 flashes Red light 7 flashes green light VDD allow stop protection
4 flashes Red light 8 flash green light reverse VDD permission stop
5 brightness Red light 2 brightness green light IPM protection
5 flashes Red light 3 flashes green light whistle unusual
5 flashes Red light 5 flashes green light compressor failure
5 flashes Red light 6 flashes green light outdoor fan failure
6 flash Red light 2 flash green light id fan motor switched off
Flash 3 id id fan motor rotation error
7 brightness Red light 2 brightness green light high discharge temperature
7 brightness Red light 3 brightness green light high pressure
7 Glow Red light 4 Glow green light 4-Way Valve Uncommon
7 flashes Red light 5 flashes green light pressure switch failed
7 brightness Red light 6 brightness green light compressor temperature error
8 flashes Red light 2 flashes green light active filter AFM failed at first time
8 flashes Red light 3 flashes green light active filter AFM fail 2 times
8 flash Red light 4 flash green light PFC circuit error
Blinking pcb failure
Fujitsu Air Conditioner Troubleshooting
In the event of a malfunction (burning odor, etc.), immediately cease operation, disconnect the power supply plug, and consult with authorized service personnel. Turning off the power switch of the unit will not disconnect the unit completely from the power source. Always make sure to disconnect the power supply plug or close your circuit breaker to ensure that the power is completely off.
Before requesting service, do the following checks:
Symptoms: does not work immediately
If the unit is stopped and then immediately restarted, the compressor will not operate for approximately 3 minutes, to prevent fuse blowouts.
Whenever the power supply plug is disconnected and then connected to the power outlet, the protection circuit will operate for approximately 3 minutes to prevent unit operation during that period.
Symptom: noise is heard
During operation and soon after stopping the unit, the sound of water flowing into the air conditioner’s piping can be heard. In addition, the noise may be particularly noticeable for about 2 to 3 minutes after starting the operation (sound of coolant flowing).
During the operation, a slight scream can be heard. This is the result of minute expansion and contraction of the frontal extension due to temperature changes.
During heating operation, sometimes a burning sound can be heard. This sound is produced by automatic defrosting operation.
Problem: Some odors may be emitted from an indoor unit. This smell is the result of room odor (furniture, tobacco, etc.) that has been taken into the air conditioner.
Symptoms: mist or steam are emitted
During cooling or dry operation, a thin mist may be seen from the indoor unit. This results from the sudden cooling of room air by the air emitted from the air conditioner, resulting in condensation and mist.
During heat operation, the fan of the external unit may turn off, and steam can be seen rising from the unit. This is due to the automatic defrosting operation.
Symptoms: airflow is weak or stops
When heat operation is initiated, the fan speed is temporarily too low to heat the internal parts.
During heating operation, if the room temperature rises above the thermostat setting, the outdoor unit will shut down, and the indoor unit will operate at a much lower fan speed. If you want to heat the room further, set the thermostat to a higher setting.
During heating operation, the unit will temporarily stop opera (between 7 and 15 minutes), with defrosting mode operating automatically. During automatic defrosting operation, the operation indicator lamp will flash.
During dry operation or when the unit is monitoring room temperature, the fan may run at very low speeds.
During super qubit operation, the fan will work at very low speed
In monitor auto operation, the fan will operate at a very low speed.
Characteristics: Water is produced from external unit
Problem: During heating operation, water can be produced from the outdoor unit due to automatic defrosting operation.
Symptoms: AIR CLEAN Indicator Lamp (Green) will start flashing slowly (as shown in the figure):
Problem: After about 400 hours of air cleaning mode usage, the AIR CLEAN indicator lamp will start to glow slowly (as shown in the figure). When this happens, please shut down the system, remove the main socket and perform maintenance on the air filter of the dust collecting unit.
Symptoms: AIR CLEAN Indicator Lamp (Green) will light up quickly (as shown in the figure):
Problem: After about 500 hours of air cleaning mode use, the AIR CLEAN indicator lamp will start flashing quickly (as shown in the picture). At this point, the air cleaning will stop working. Please shut down the system, remove the main socket and perform maintenance on the air filter of the dust collecting unit.
Symptoms: Does not work at all
Has the power supply plug disconnected its outlet?
Is there a power failure?
Is the fuse blown, or is the circuit breaker tripped?
Is the timer working?
Characteristics: The unit operates in a different way from the setting of the remote control unit
Are remote control unit batteries dead?
Are the batteries in the remote control unit properly loaded?
You May Also Read